K&D Factory Service Inc. bas been bringing OEM commercial cooking parts and service to restaurants and commercial kitchens of Grantville, PA and the surrounding areas since 1945!
Read our reviews and find out why your colleagues consider us to be their nearby commercial cooking supply company in Grantville, PA.
for Grantville, PA
Our Reviews by City
Turned unit on and checked operation. Found suction pressure starts high (45 psi) and stays there for a couple minuted and then drops to 15 pis/ CRO valve stem turns but is has no effect on pressure or amp draw. Valve is bad and needs replaced. I also caught start relay sticking once causing unit to draw 56 amps and this lasted for a few seconds. I also noticed molex plug for compressor power cord burned. I would recommend replacing start components and cord. Will quote repairs
Service Check-In ..
Rational Combi-Oven Tech - Per customer drain discharge hose broke and soaked bottom convection blower motor and combustion blower. Also gas valve module assembly and was tripping ground fault. Customer dried components and now gas error. Swapped parts with other unit and found it also has 2 bad modules. Finally got all burners to fire with good ignition and flame current but only in function test. Customer will find another module tomorrow