K&D Factory Service Inc. bas been bringing OEM commercial cooking parts and service to restaurants and commercial kitchens of Ebensburg, PA and the surrounding areas since 1945!
Read our reviews and find out why your colleagues consider us to be their nearby commercial cooking supply company in Ebensburg, PA.
for Ebensburg, PA
Our Reviews by City
Ebensburg - Ebensburg, PA
Ebensburg - Ebensburg, PA
ROB dripping grease or oil - per customer via phone: Found substance leaking out not to be grease but a buildup of product due to seals wear letting product leak past bowl. Customer had new seals. Installed new seals. Customer would like new seals to have on hand for all three units.
Found Walk-In Freezer box temp 39 degrees. Sight glass empty and has leak dye in system. Charge with 4lb 8ozs r404a to full sight glass. Pressures ok. Leak checked and found all joints have been soft soldered. Found leak at suction line connection to coil. Leak detector is also sounding in and around evap coil but could be due to suction leak. Will need to replace line set and hold nitrogen on system to see if any more leaks are present. Will estimate repairs. Charge on system may not last a week.
Found Walk-In Cooler evap fans running box temp at 70 degrees. Condensing unit is off on low pressure control. Found system to have no refrigerant left in it. Charged with 250 psi nitrogen and found coil is still leaking on loops and now distributor has a huge leak in it. Will quote new evap coil and installation.
Found Reach-In Cooler unit on and cabinet temp at 51 degrees. Found evap coil froze up. Checked and found probes faulty will need new probes. Also right door not closing customer stated it was a new door. Found gasket is slightly different from original door. Shimmed out hinges to make door close correctly. Spoke with Bernie about probes and he gave the okay to order qwp (expedited freight). 7/17/20 Removed faulty probes and installed new probes. Tested values and reading okay. Started and ran down to setpoint okay. Ran defrost cycle okay. Did see where door switch sometimes is not fully engaged shimmed switch and tested okay.
Delime steamer #3: used delimer to descale boiler bases. pumped cleaner through steamer for an hour and flushed with clean water. no leaks found and unit running okay. Will start new work order for repairs.
Found Reach-In Cooler unit on and running at 55 degrees. Checked amp draw on compressor it was low. There was a low side access port in unit found unit running in a vacuum. Pulled apart evap section and condensor section and tested for leaks found leak upon braze joint on heat exchanger. Cannot work on u it where it is located will take to shop and repair and return. Compressor was running very hot but will not know if any other components were damaged until leak is fixed and I it is recharged and running. 02/06/2019 Removed charge from system. Removed filter drier and I stalled new drier. Fixed leak on heat exchanger connection. Charged with 110 lbs nitrogen and held for 20 min. ok no leaks. Pulled 500 micron vacuum and then charged with 110 grams R290 factory charge. Ran and cycled several times and watched pressures ok. Helped Sean with unit. 2-7-19 Returned cooler and set back in place ran power cord back thru chase and plugged in. Ran and cycled cooler at 33 degrees ok.