K&D Factory Service Inc. has serviced commercial refrigeration & commercial kitchen equipment in Altoona PA since 1945.
Call us now at: 1-800-932-0503 or check out why commercial kitchens turn to K&D Factory Services for our top-rated commercial cooking equipment, parts and repair needs in Altoona PA.
for Altoona, PA
Our Reviews by City
Removed Dishwaher cracked suction hose and installed new hose. Tested for leaks, found none.
Removed Dishwasher leaking wash pump motor and installed new pump and motor assembly. Ran, tested rotation and for leaks, all okay.
Found unit off. Found split rinse hose from booster. Replaced with truck stock. Ran. Found 60 PSI on rinse. Set point should be 20-25PSI. Unable to adjust regulator. Found difficulty getting unit to start. Was shown that they cycle power on and off and it starts up. Found booster gaskets leaking past. Likely due to high pressure. Will obtain parts and return. 5/15/18 Replaced pressure regulator, booster hose and plumbing. Removed booster elements and installed new gaskets. replaced booster cover. Ran unit and checked rinse temp and pressure and all okay. unit okay at this time.
(SATURDAY CALL OUT) Upon arrival found evap fans running. Compressor running, also condenser fan running. Evap coil solid ice. Customer was not turning unit off at night and there is no lid for cooler "prep area". Needs to be turned off at night to defrost until Customer can get lid for top. Will stop in Monday AM to check over, Unplugged compressor for tonight so coil will thaw.
Found unit at 50*F upon arrival and compressor not running by 115v, going to start components. Removed start components and installed 3 n 1 start package. Comp. runs at 6 amps and unit cycled at 39*F. Set t-stat end cycled unit at 33*F. T-stat was very tight. Will order new start components and t-stat. (Parts on order at United 7-18-16.) -- Returned to replace start components per parts order. Tested, working at this time.